Automatic Sprinklers Storage Cabinet
A building with sprinklers must keep a minimum supply of six spare sprinklers on the premises, so personnel can replace any sprinklers that have activated or that have been damaged in any way. The number of spares in supply corresponds to the number and types of sprinklers in the building.
Building managers should keep the spares in a cabinet located where the temperature will never exceed 100o F. The cabinet should also contain a special wrench used for removing and installing sprinklers. There must be one wrench for each type of sprinkler installed.